What do I do if my Solar Panels aren’t working?
To save you waiting for us to get to you and the possibility of a call out fee if the fault is not covered by any warranty, it’s worth going through a few checks of your own first. Here’s what you need to do:
- The classic IT ‘Powercycle’ is always a good start, turn all the switches off, leave it 30 seconds and turn them all back on again. Remember your inverter will take 3 minutes to start up before it starts generating.
- Check your inverter screen. Is there an error message? If yes, take a photo of it. This will help with the diagnosis and the message may disappear after a time.
- If the inverter screen is blank, is it dark outside? Most inverters won’t liven up unless your solar panels are generating. If there is enough light outside for the panels to generate and the inverter screen is not showing anything then there’s a good chance there’s no grid supply to the inverter.
- Check all MCBs (miniature circuit breakers) and RCDs (Residual Current Detectors) to ensure they’re all in the ON position (up). RCDs may trip to a mid position and may need to be pushed all the way down before they can be pushed in to the up position and stay there.
- Check the Total Generation Metre (TGM). If there’s a solid red LED then there is grid power to the TGM but nothing is being generated. If the TGM’s Red LED is blinking then the system is generating. The rate of the blink is determined by the power the panels are generating. If it’s a really dull day then it may only blink once every 20-30 seconds, so check carefully. If the sun’s out in full then the blinking may occur more than once a second. If the screen of the TGM is blank and the Red LED is never blinking then it looks like there is no grid power to the TGM.
- Check your AC & DC Isolators. These are near your inverter and there may also be one near your Consumer Unit (fuseboard) if the Consumer Unit is in a different room to your inverter.
- If all the switches and isolators are on and you’re still not getting any juice from your solar PV then it’s probably time to give us a call. We’ll help as much as we can over the phone and may ask you to email any photos so we can see if we can get you up and running without having to wait for us to come out and avoid the possible costs of a call out.
There’s grid power to my PV inverter but still no generation.
You’ve confirmed there is a grid connection to the inverter but there’s still no juice. Here’s some of the more likely issues.
- These types of fault are often caused by excess moisture so may only happen on damp/wet days. It’s quite common for them to clear as the day warms up and dries any moisture out. If you’ve got monitoring on your system then you may see your system starting to generate later and later in the mornings, especially on damp or wet days.
- Your inverter is able to detect these faults so will not allow the system to generate until it is cleared. This will usually be displayed on the inverter screen too.
- These faults will need an expert to identify and may require investigation. Give us a call or email and we’ll be happy to help.
- This can happen when the system is starting up in the morning. Sticky relays in the inverter can mean too much current will flow and trip your switches in your consumer unit. You’ll need to contact us for further investigation.
- RCD tripping is caused when there is excess leakage current. RCDs are designed to prevent electrocution and can be very sensitive. Certain appliances, like PCs, electronic goods and inverters will have a small amount of leakage current in their normal operation. If several appliances combine on the same RCD then nuisance tripping may occur. Try turning off different devices to see if you can identify the cause using a process of elimination. If you still can’t fathom out the cause then give us a call or email.
If your inverter is underperforming or near its sell by date, it might be a good time to consider upgrading to a SolarEdge system. SolarEdge inverters and optimisers have many features which automatically identify problems often before you even know about them. They can also be set up to alert Naked Solar where we can often fix the problem remotely.
SEE OUR SOLAREDGE GUIDE
Still not working?
If none of the above gets your system back up and running then we can help. To speed things up and help us get to the problem with the least time, cost and fuss then either call us on 01637 697009 or email firstname.lastname@example.org with a description of what’s happened and photos of the following:-
- The inverter screen with any messages that come up (error codes, RISO faults etc).
- The sticker on the side of your inverter that has the serial number, make & model.
- Your overall inverter set up, from a distance so we can see the whole installation and it’s vicinity.
- All Consumer Units (fuseboards) in the property, close up to show circuit labels and stood back showing the location.
- Total Generation Meter.
- The schematic diagram that should be near your inverter.
- Any cables that go from your inverter to your panels.
- Your solar panel array/s.
- If it is possible, a picture of underneath the panels or the gap between the panels and the roof (we’re looking for loose cables).
It would also be useful if you’re able to include the following information:-
- Copy of MCS certificate.
- Make & Model of panels (if no MCS certificate).
- Date of installation (if no MCS certificate).
- Size of installation in kWp (if no MCS certificate).
- History of any other faults or issues including the weather conditions at the time of the fault/s.
Once we have this information we’ll initially contact you to discuss possible issues and likely costs of investigations and solutions (if not covered by any warranties). We can also answer any questions and concerns you have.
Other useful contacts:
SolarEdge support 0800 028 1183 email@example.com
My Energi support 0333 300 1303 firstname.lastname@example.org
SMA inverter support 01908 304899 email@example.com
Aurora Power One support 01903 823323 GB-Solar.firstname.lastname@example.org
Tesla Energy support 0800 0988064 email@example.com
Solis inverter support 0113 328 0870 firstname.lastname@example.org
Sola X support 02476 586998 email@example.com
Marlec support 01536 201588 firstname.lastname@example.org